Table 2-1 Unit Maintenance Checks and Services Monthly Schedule (CONTINUED)
Item to be
If any flowmeter or pressure gage is inoperative, schedule
for repair or replacement. Ensure that connections are tight,
valve handles can be operated, and vents are operative before
repairing or replacing.
Inspect pulleys for wear and damage. If pulley is bent or worn,
replace. Straighten dents in belt guard, repair as needed,
and replace guard if damaged beyond economical repair.
Clean and treat pump motor connectors and wiring with
approved corrosion control substance after every 1000 hours of
Remove motor top cover plate and conduit box covers;
clean and treat wiring and connectors with approved corrosion