3-54. INJECTION PUMP REPLACEMENT (CONT)
With governor control lever in shutoff position, place spacer over rod that makes contact with rack.
Put force on rod that makes contact with rack, to hold spacer in position while dial indicator setting is made.
Place dial indicator on zero. Take spacer away from rod that makes contact with rack.
Using circuit tester, connect clip end to brass terminal on governor housing.
Place other end of tester on good ground.
Turn governor lever in FUEL-ON direction until test light comes on.
Move governor lever toward SHUT-OFF position until test light goes out.