Table 2-13. Operator Preventive Maintenance Checks and Services (PMCS)
Not Fully Mission Capable If:
a. Check for loose mountings and
Damaged electrical cables.
cracks in housing.
b. Inspect for loose or broken air lines and
damaged electrical cables.
c. Check for loose or broken indicator
a. Inspect for loose or missing mountings
Cracked vessels or piping or leaking
end cap seals.
b. Inspect for cracks and damage to vessel
housing and piping.
c. Check for damaged drain lines and
a. Inspect for cracked piping and product
Cracked piping or manifold.
b. Inspect for broken vents, drains, or
Air Tank and
a. Inspect for broke, loose, or missing
Missing mounting brackets and fittings.
mountings and air fittings.
b. Check for missing bottle guard.
c. Inspect for broken drain cock.
Check for loose or missing mountings,
Loose or broken tubing or missing
tubing, and knobs.
Inspect for missing or damaged bolts, nuts,
Damage that would prevent operation.
weather seals, and caps.
JB1 and JB3
a. Inspect vessel and piping for leaks.
Damage is observed or any leaks are
b. Every 100 hours check high pressure
pump hourmeter and replace carbon and
a. Inspect for leaks at connection points.
Class III leaks are found.
b. Check for excessive vibration, broken
vents, and drain lines.
Check for air leaks and clogs.
Air leaks found.
a. Check for Eyewash operation.
Eyewash does not operate or pressure
b. Check to make certain pressure gage
is less than 85 psig (586 kPa).
reads 90 psig (621 kPa) (para. 3-5).
2-44 Change 12