Figure 4-38. Raw Water Pump External Electrical Panel Assembly (sheet 2 of 3) Components
m. Refer to sheet 1 and remove two conduit nuts (46).
n. Pull harness assemblies (47 and 48) out of the box with nuts (49), retainers (50), bushings (51), bodies (52) and
sealing rings (53) attached.
o. Loosen nut (49) and slide items (49 thru 53) off harnesses (47 and 48).
a. Replace any damaged or missing components.
b. Replace damaged ring tongue connectors (para. 4-10).
c. Replace damaged nameplates (para. 4-10).
d. Replace missing or damaged wire markers (para. 4-10).
e. Replace damaged rivnuts (para. 4-10).
f. Replace gaskets showing signs of leakage.
g. Replace desiccant cannister (54) if desiccant has changed from pink to blue.