b. Install sight indicators (14) with clamps (21). Be sure indicators(14) are located in relation to the marks made
during disassembly and that the marked tops of the indicators are at the top of the assembly.
Arrow on float must point up.
c. Install float(13) with arrow pointing up, gasket (12), cap (11) and secure in place with clamp (10).
d. Install tee (9), fining (8), nipple (7) and valve (6). Be sure to cover all male threaded surfaces with antiseize tape,
wrapped clockwise when viewing the fining.
a. Install chamber (5) using capscrews (1), lockwashers (2), washers (3) and nuts (4).
b. Connect tubing at top of chamber (5) and at fitting (8). Tighten tubing compression nuts.
c. Connect plugs on level switches to power cables.