Figure 2-31. Testing Ground Fault Indicator
Adjustment of the motor starter resets is as follows (refer to Figure 2-31.1).
Length is measured from inside panel door to outside of contactor face.
To shorten, rotate threaded bushing (4) counterclockwise, then rotate threaded shaft (5) counterclockwise to
match length in Table 2-2.
To extend, rotate threaded bushing (4) clockwise, then rotate threaded shaft (5) clockwise until correct dimension
is met as shown in Table 2-2.
Length ± .25 in. (6.35 mm)
8.00 in. (203 mm)
Raw Water Pump
7.5 in. (191 mm)
6.00 in. (152 mm)
7.25 in. (184 mm)
8.25 in. (210 mm)
Figure 2-31.1. Reset Mechanism Adjustment
2-132 Change 1