Set CHLORINE valve to RUN position (fig. 2-66).
The ROWPU is now in full operation. Check the TDS of the product water (para. 2-32c), record the findings
in operators log. If reading is above 1500 ppm, refer to Section II, Chapter 3, Troubleshooting. Keep watching your gages
and lamps. Complete the operators record (log) hourly. Refer to Table 2-4 for normal and trouble point indications.
Periodically check the brine tank.
Full? Up to 3 inches from top?
When brine tank is full, remove the canvas brine hose coming from the ROWPU and allow to drain on
Ensure that the drained brine water runs towards lower ground as far
from the raw water source as possible.
Let brine flow on the ground until after next backwash, then put the hose back into tank.