2-25. CABLE ASSEMBLY W45 (DISTRIBUTION PUMP) MAINTENANCE - continued.
Wire insulation can be damaged when wires are pulled through conduit box.
Be careful when pulling wires.
Position cable wires in conduit box (7) and tighten sealing grip (15).
There are three sets of motor wires to connect to power source. Each wire
from the power source is added to a motor wire set in the same way. One is
Remove nut (13), lockwasher (12) and flat washer (10) from screw (9).
Install colored wire (11) from power source as tagged, lockwasher (12), and nut (13) on screw (9).
Position grounding wire (16) in conduit box (7) and secure with screw (17).
Using electrical tape (8), wrap each wire set (6).
Secure electrical tape (8) on each wire set (6) with twine (14).
Position bundle of four wire sets (6) in conduit box (7).
Position gasket (5) and conduit box cover (4) on conduit box (7). Install four screws (3).
Wrap cable assembly (1) on distribution pump assembly frame (2).
Start distribution pump and check for proper operation (TM 10-4610-240-10).