FLOW METER (BRINE WATER) MAINTENANCE - continued.
Apply antiseize tape to all male pipe threads. Be sure tape is wrapped in same direction as threads.
Install pipe sections (18 and 3) on flowmeter (19) as tagged.
Position flowmeter (19) face in cutout on control panel (21). End of pipe section (3) must extend through
control panel cutout.
Position bracket (15) on two studs (20) and install lockwashers (16) and nuts (17).
Install gasket (14), clamp halves (12), two screws (13), and nuts (11).
Piping can be badly damaged by corrosion if pipe section and ring filler are in contact. Be sure that
insulating tape separates pipe section and ring filler.
Install insulating tape (7) and ring filler (2) on pipe section (3) where two-piece strap (4) will clamp.
Position two-piece strap (4) on pipe section (3) and install two screws (5), flat washers (8), lockwashers (9)
and nuts (10).
Tighten two nuts (6).
Install cap (1) on pipe section (3).
Operate ROWPU (TM 10-4610-240-10). Check for leaks and proper operation.