2-65. HIGH PRESSURE SWITCH MAINTENANCE - continued.
a. Apply anti-seize tape to all male pipe threads of adapter (7) Be sure tape is wrapped in same direction as pipe
b. Install adapter (7) on high-pressure switch (13).
c. Install adapter (12) on high-pressure switch (13).
d. Position high-pressure switch (13) on control panel (9) and install two screws (10), flat washers (14), lockwasher
(15), and nuts (16).
e. Thread cable assembly wiring through adapter (12) and tighten sealing grip (11).
White wire connects to C terminal. Blue wire connects to NC terminal.
f.. Install three wire lugs (8) and screws (5) as marked during removal.
g. Install gasket (1), cover (2), four starwashers (3) and four screws (4) on high-pressure switch (13).
h. Operate ROWPU (TM 10-4610-240-10). Check for proper operation for leaks.