Table 3-1. Direct Support Troubleshooting - continued
TEST OR INSPECTION
ROWPU ASSEMBLY - continued
ITEM PLUGGED INTO UTILITY RECEPTACLE DOES NOT WORK.
High voltages in this equipment can cause serious injury or death. When
applying power during a test, take proper measures to ensure personal safety.
Never work on electrical equipment unless there is another person nearby who is
familiar with the operation and hazards of the equipment and who is competent in
administering first aid.
Remove item, connected to outlet and check if RESET button on electrical outlet is IN.
If reset button is popped out, reset circuit by pressing IN. If it pops again, replace outlet assembly
Check for 115 VAC at outlet.
If 115 VAC is measured, troubleshoot Item disconnected from outlet..
Check if 208 VAC, three phase power is available at generator output lugs.
If power is not available, refer to power source manual.
Check for 115 VAC at power cable P1/P10 between pins N (ground) and B.
If power is not available, repair power cable assembly Refer to paragraph 3-23.
Perform a point-to-point continuity check of power circuit.
If continuity is absent between external connections of UTILITY OUTLET receptacle, J7 and
corresponding outlet contacts, replace outlet assembly. Refer to paragraph 349.
If continuity is absent in wiring, tighten loose connections or repair/replace defective wire.