3-26. ELECTRICAL CABLE W46 (HIGH PRESS SWITCH) MAINTENANCE.
This task consists of:
General Mechanics Tool Kit (Appendix B, Section III, Item 4)
ROWPU shut down (TM 10-4610-240-10).
Power shut down (power source manual)
General Safety Instructions
High voltages in this equipment can cause serious injury or death. Be certain that
all power is removed before performing maintenance.
ELECTRICAL, CABLE W46 (HIGH PRESSURE SWITCH)
Remove four screws (9), lockwashers (8) and remove cover (7) and gasket (6) from high pressure switch (4)
Tag all wires before removal.
Remove three screws (10) and three wires (11)
Loosen nut (2) from adapter (3)
Remove locknut (5) and pull cable assembly (1) from high pressure switch (4)
Working at electrical junction box loosen nut (12)
Tag all wires before removal
Remove three screws (19) and three wires (20) from terminal board (21)
Remove locknut (18)