2-26. OPERATION IN NUCLEAR, BIOLOGICAL, OR CHEMICAL CONTAMINATED
AREAS - cont.
Connect dispensing nozzle to end of discharge hose.
Connect distribution pump electrical cable to DISTRIBUTION PUMP receptacle on junction box.
Connect raw water pump No.1 electrical cable to RAW WATER PUMP NO. 1 receptacle on junction
Ensure all seals are in place and quick disconnect coupling are locked.
Check security of all coupling connections.
Set CHLORINE RUN/PRIME valve (figure 2-60) to PRIME position.
Disconnect chemical feed hoses from CHLORINE chemical can (figure 2-42).
Remove lid (figure 2-41) from CHLORINE chemical can and insert chemical feed hoses into top of
can. Make sure suction hose (female quick disconnect fitting) is not submerged in the chlorine
During NBC operation, manually chlorinate product water tank No. 2. You MUST check with base medical
personnel for safe chlorinating instructions.
With exception of the CHLORINE chemical feed pump, operate the ROWPU using normal operating
To prevent injury to personnel, deionization cartridges must be replaced after 100 hours of use.
(Model WPES-10) The generator set hourmeter may be used to record start, stop and operating
time of deionization cartridges.
After 100 hours of use, remove both deionization cartridges and replace with new cartridges.