2-7. ROWPU ASSEMBLY AND PREPARATION FOR USE - cont.
Install Raw Water Pump No. 1 Quick Disconnect and Strainer Fittings. Refer to figure 2-26.
· During installation, apply antiseize tape (from storage chest) to pipe threads of quick disconnect
· Raw water pump No. 1 uses both a male and female quick disconnect fitting. Raw water pump
No. 2 uses two female quick disconnect fittings.
If required, mark frame of one raw water pump as "No. 1".
Unscrew plugs from suction and discharge couplings.
Install 1 1/2-inch female quick disconnect fitting on suction coupling.
Install 1 1/2-inch male quick disconnect fitting on discharge coupling.
Close drain and vent valve on raw water pump No 1.
Install 1 1/2-inch male quick disconnect fitting on raw water strainer.
Figure 2-26. Raw Water Pump No. 1 Quick Disconnect Fittings.