CABLE ASSEMBLY, W40 (GENERATOR) REPLACE (MODELS WPES-10) - continued.
The following test is performed to determine if the cable assembly is
defective. Cable assembly must be disconnected. Failure to disconnect
cable can result in false indications.
Make sure wire ends are not touching each other.
Using multimeter, test cable assembly (10) for continuity between sockets of cable connector (12) and
ends of wires.
CABLE ASSEMBLY W40 CONTINUITY TEST
If continuity does not exist between any two points, notify Direct Support Maintenance.