Table 3-1. Direct Support Troubleshooting - continued
TEST OR INSPECTION
ROWPU ASSEMBLY - continued
UTILITY OUTLET CIRCUIT BREAKER (CB8) FAILS TO RESET.
High voltages in this equipment can cause serious injury or death. When applying power
during a test, take proper measures to ensure safety of personnel. Never work on
electrical equipment unless there is another person nearby who is familiar with the
operation and hazards of the equipment.
Disconnect external device connected to UTILITY OUTLET receptacle, J7. Reset UTIL OUT circuit
If UTIL OUT circuit breaker does not trip, repair connected device.
Remove power at power source and disconnect wire lead from UTIL OUT circuit breaker, terminal T.
Reset UTIL OUT circuit breaker and apply power.
If UTIL OUT circuit breaker trips, replace circuit breaker. Refer to Paragraph 3-53.
Remove power at power source, reconnect open wire, disconnect wires connected to UTILITY OUTLET
and check for continuity between power and ground contacts on outlet.
If continuity exists, replace utility outlet receptacle. Refer to Paragraph 2-73.
Check for bare/disconnected wiring in junction box.
Reattach loose wires or replace defective wire.