Table 3-1. Direct Support Troubleshooting- continued
TEST OR INSPECTION
CHEMICAL FEED PUMP - continued
If continuity is absent through K7, replace motor starter. Refer to Paragraph 3-61.
If continuity is absent through circuit breaker, CB7 (CB7 ON), replace CB7. Refer to Paragraph 3-
If continuity is absent in wiring, tighten loose connections and/or replace defective wire.