Table 3-1. Direct Support Troubleshooting- continued
TEST OR INSPECTION
CHEMICAL FEED PUMP - continued
If continuity does not exist through cable assembly, W-52, repair cable. Refer to Paragraph 3-27.
If continuity does not exist through K7 contacts and/or 450-600 Ohms is not measured between Al
and A2, replace motor starter. Refer to Paragraph 3-61.
If continuity does not exist through wires, tighten loose connections and/or replace defective wires.