3-30. CABLE ASSEMBLY, W56 (TDS POWER) REPAIR.
This task consists of:
General Mechanics Tool Kit (Appendix B, Section III, Item 4)
Multimeter (Appendix B, Section III, Item 3)
Refer to TM 43-0158/TO 1-lA-15 (Air Force) for Tools required to inspect and repair
Rags, Wiping (Appendix C, Section II. Item 14)
Lockwashers, Seals and Gaskets (TM 10-4610-241-24P)
Tiedown Straps (TM 10-4610-241-24P)
Refer to TM 43-0158/TO 1-lA-15 (Air Force) for Materials required to inspect and repair
Power shut down (Power Source Manual)
TDS Monitor disconnected from ROWPU (TM 10-4610-241-10).
Junction Box open (Paragraph 3-53).
General Safety Instructions
High voltages in this equipment can cause serious injury or death. Be certain
that all power is removed before performing maintenance.
Remove screws (1) and disconnect three wire lugs (2) of cable cable assembly (10); black, white and green,
from TB4 (3), contacts 1, 2 and 3.
Unscrew nut (4) from adapter (6).
Remove nut (4).
Pull cable assembly (10) with nut (9), seal ring (8), seal (7), adapter (6) and gasket (5) from junction box (11).