3-36. CABLE ASSEMBLY, W57 (DISSOLVED SOLIDS SENSOR) REPAIR.
This task consists of:
General Mechanics Tool Kit (Appendix B, Section III, Item 4)
Multimeter (Appendix B, Section III, Item 3)
Refer to TM 43-0158/TO 1-lA-15 (Air Force) for Tools required to inspect and repair
Rags, Wiping (Appendix C, Section II, Item 14)
Lockwashers, Seals and Gaskets (TM 10-4610-241-24P)
Tiedown Straps (TM 10-4610-241-24P)
Refer to TM 43-0158/TO 1-lA-15 (Air Force) for Materials required to inspect and repair
Power shutdown (Power Source Manual).
General Safety Instructions
High voltages in this equipment can cause serious injury or death. Be certain
that all power is removed before performing maintenance.
Unscrew nut (1) and remove sensor (2) from product water pipe (3).
Remove gasket (4) and packing (5) from sensor (2).
Remove four nuts (6) lockwashers (7), washers (8), screws (9) and dust cap (10) from control panel.
Unscrew cap (10) from cable assembly (17).
Remove cable jack (11) from cutout in control panel and remove gasket (12) from jack.
Remove nuts (13), lockwashers (14), screws (15) and two clamps (16), securing cable assembly (17) to
As required, remove adapter (18) from pipe section (3)