Table 2-2. Unit Troubleshooting - continued
TEST OR INSPECTION
RAW WATER PUMP NO. 2 ASSEMBLY
PUMP ASSEMBLY IS NOISY.
Notify Direct Support Maintenance if this malfunction occurs.
PUMP ASSEMBLY RUNS HOT.
High voltages in this equipment can cause serious injury or death. When applying power
during a test, take proper measures to ensure safety of personnel. Never work on
electrical equipment unless there is another person nearby who is familiar with the
operation and hazards; of the equipment.
Step 1. Turn circuit breakers CB3 and CB4 to OFF and disconnect both raw water pumps at
Step 2 Connect raw water pump number 2 to RAW WATER PUMP NO 1 jack, J3 and turn on
If pump does not run hot now, ROWPU is defective, notify Direct Support Maintenance.
Step 3. Turn CB3 to OFF and disconnect raw water pump no.2 at junction box.
Step 4. Disconnect pump cable assembly at motor of raw water pump no. 2 (Paragraph 2-19)
and check for shorts.
If defective (shorted), replace cable assembly. Refer to Paragraph 2-19.
If cable assembly is not defective, replace centrifugal pump of raw water pump no. 1. Refer to