SECTION III. OPERATION UNDER USUAL CONDITIONS.
2-7. SITING REQUIREMIENTS. The hypochlorination unit should be situated so that it Is stable, and allows for free
movement by operator around equipment during operation It should also be situated so as to prevent hypochlorite
solution from spilling from reservoir.
2-8. ASSEMBLY AND PREPARATION FOR UJSE.
Remove packing material from hypochlorination unit
Remove and retain technical publications envelope
Waste water line must not be elevated or restricted In any way
Remove packing material from waste water hose, and extend waste water hose to full length Ensure waste water
hose is going to suitable drain location and that discharge of hose is at level lower than chemical pump. Also,
secure drain end of hose, as it may jerk when water Is discharged
2-9. INITIAL ADJUSTMENTS AND CHECKS.
Remove cover, check condition of gasket ii female camlock, and replace if necessary Use camlocks to install
hypochlorination unit in water distribution system as detailed in appropriate system manual
Check to ensure dosage dial Indicator is at position 5, as shown below It may be necessary, to change position
at a later time, but you should start operations at position 5