Set stroke adjusting knob (2) at position 5 as read on dial scale assembly (1).
Check that foot valve (3) is in reservoir (6) about 1 inch from bottom.
Close drain cock (5) on water meter (4).
Release locking tab (10) on inlet ball valve (8) and position valve in the closed position.
Position outlet ball valve (7) and reservoir fill valve (9) in the closed position.
Figure 2-3. Initial Adjustments
2.7.1 Starting Procedures. Start up and operating procedures are as follows (Refer to Figure 2-6):
Start system water flow. Refer to applicable system manual.
Lift locking tab (10, Figure 2-3) and open inlet ball valve (8).