4-31. REPLACE PRESSURE GAGE.
This task covers:
a. Tools. Tool Kit (Appx B, Sect Ill, Item 1).
b. Materials/Parts. Tape, Antiseize (Appx E, Sect II, Item 4).
c. Equipment Condition. Hypochlorination unit removed from water supply line.
Remove pressure gage
(1), brass elbow (2), and brass nipple (3).
Inspect pressure gage, brass elbow, and brass nipple for damaged threads and cracks. Replace as required.
Apply Antiseize tape to all metal to metal pipe connections.
Install pressure gage (1), brass elbow (2), and brass nipple (3).
END OF TASK