When display page appears on video monitor, take one of these three actions.
Push keyboard key 1 (prompt ADVANCE CURSOR) to move cursor to select new switch.
Push keyboard key 3 (prompt SELECT NEW PAGE) to select a new display page.
Push keyboard key 4 (prompt RETURN TO EDIT MENU) to return to EDIT MENU.
8-126.96.36.199 Using EDIT MENU option 3 to activate/deactivate totalizers
Totalizers are activated/deactivated for the same reason and in a similar manner to
activating/deactivating sensors in paragraph 8-9.4.2. Deactivating a totalizer stops
main processor from monitoring that particular switch. Deactivation may be
necessary when a totalizer is malfunctioning, is displaying false information on
video monitor screen display page and is activating alarms when no problem
exists. When a totalizer is deactivated, the word DEACTIVATED appears in place
of the totalizer emblem on video monitor. After totalizer has been repaired or
replaced, totalizer is reactivated. The word DEACTIVATED disappears and totalizer
emblem again appears on video monitor.
Push keyboard key 3 (EDIT MENU option ACTIVATE/DEACTIVATE/PRESET TOTALIZERS). Make sure
page select prompt in step 8-188.8.131.52 a appears on video monitor.
Push POTABLE WATER TANKS keyboard key that shows TOTAL TANKS totalizer data (Figure 8-3).
Make sure display page chosen is shown on video monitor.
If highlighted instructions called "prompts" shown below are displayed on the screen and totalizer
is double intensity, go to step c.
EDIT THIS ONE
SELECT NEW PAGE
RETURN TO EDIT MENU
If screen flashes, indicating display page has no totalizer, either press another display page key
or press EDIT key to return to EDIT MENU.
Push keyboard key 1 (prompt ADVANCE CURSOR) and move cursor to totalizer to be activated/
Push keyboard key 2 (prompt EDIT THIS ONE). Make sure video monitor displays totalizer information
with totalizer label at top of page and prompts in upper right comer. Make sure cursor is on the line with
Push keyboard key 2 (prompt EDIT THIS ONE) again. Make sure cursor extends all the way to the right.
When totalizer is deactivated, letter "X replaces numbers to indicate totalizer is no
longer counting. After totalizer is repaired or replaced, totalizer is reset to agree
with flow meter reading and then is reactivated. Letter "X" is replaced with input
To activate totalizer, push keyboard key 0 and to deactivate totalizer, press keyboard key 1.