CHLORINE STATUS display page (Figure 9-12)
SYSTEM STATUS display page (Figure 9-13) - check the following:
CHLORINATOR OPERATING OFF is normal
CHLORINATOR PWR SUPPLY FAIL is normal
BRINE RCIR PMP OPERATING OFF is normal.
If these indicators are not as listed in step n, take corrective action.
If EMS alarms indicate abnormal conditions, acknowledge alarms according to instructions below and take
If abnormal condition occurs, EMS activates horn and strobe light in ROWPU
space. In addition, EMS keyboard alarm sounds and EMS video monitor
automatically switches to ALARM page which shows abnormal condition in
flashing double intensity. The affected keyboard key, CHLORINE STATUS or
SYSTEM STATUS, flashes red.
Press red flashing key on keyboard to change ALARMS display page back to CHLORINE STATUS or
SYSTEMS STATUS display pages.
Press ACK key on keyboard to stop alarms, to automatically change red flashing key to white, and to
change flashing display on video monitor screen display page to double intensity.
Display stays double intensity until abnormal condition causing alarm is corrected.
During operation, perform following during operation checks:
Check for leaks, paying special attention to joints, valves, fittings, and piping. Report leaks to shift leader
for corrective action.
Check for loose of missing securements and fasteners. Tighten or replace as necessary.
Check wiring for loose connections. Tighten as necessary. Be alert to unusual noises or overheating that
might indicate a pending malfunction.
Make sure all components operate normally.