Manifold venting of two or more units through a single,
enlarged ventline is acceptable ONLY if an inline blower
of sufficient volume is installed downstream from the
toilets to be in operation in conjunction with either or
both toilets. The volume of the downstream blower must
be sufficient to provide 200 CFM through each unit with
the unit blowers on. An example: two units in tandem
will require an inline blower volume of 100 CFM.
Size of ventline also increases with the number of units
in manifold. For each pair of units add two inches to the
diameter of the vent pipe and manifold. For example.
two units require a six inch ventline whereas four units
require an eight in, h ventline.
INSTRUCTIONS AS TO USE SHOULD BE
CLEARLY VISIBLE. IF NECESSARY. THE
POTENTIAL USER SHOULD BE SHOWN
PERSONALLY HOW TO USE THE BOWL
LINER AND HOW TO FLUSH.
Hang Bowl Liner Holder.
configuration required as well as the necessary space
for use and for flushing the INCINOLET.
Bolt Mounting Plate To Floor.
Mounting plate must be leveled to offset effect of any
UNIT MUST REST ON ISOLATION
Caulk or otherwise seal the plate away from the deck to
prevent accumulation of dirt and moisture beneath the