Table 3-3. Preventive Maintenance Checks and Services for ROWPU System (Continued)
Q - Quarterly
S - Semiannually
A - Annually
CHECK FOR AND HAVE
IS NOT READY/
REPAIRED OR ADJUSTED
B D A D W M Q S A
(e) Empty and dean glass collecting
bowl on bottom d engine
crankcase filter system s fold-
Pull down on metal tab of
cage surrounding bowl.
Unsnap wire cage on each
side of bottom of bowl.
Remove bowl and wipe with
dean cloth. Do not use abra-
Replace fuel filter in reverse
Pump V Belts
To prevent electric shock, ensure battery
Is disconnected before performing this
Refer to TM 55-1930-209-14&P-2, para
6.2.10 for complete Instructions and
Illustrations on belt tensioning.
a. Check tension on pump V-belts. If they
appear to be slack adjust tension.
1) Adjust HP pump Vet as
Remove 32 mounting bolts and
Iockwashers. Remove front V-belt
housing (two pieces).
Place a straight edge on V-belt in a
straight line with bearing bases.
Place tension meter pointer on the
line on the center of the front belt
Do not contact O-ring on tester stern.
3-32 Change 1