Check to assure that the proper electrical power is available for the systems (220/440 50/60 Hz 3 phase).* Note:
This is a very important factor as the production of Hypochlorite and salt usage is directly related to the applied electrical
current. A separate service line should be installed.
The brine tank and holding tank must be supplied with soft filteredwater at 20-60 psi. The upper limit permissible
hardness is 5 grains. Water containing an excess of hardness minerals will cause a rapid build-up of scale deposits
within the cells and associated Hypochlorite handling components.
The heat exchanger can operate with either soft or hard water.
Salt Selection.: Only food grade evaporated salt without additives should be used in the brine system.
* Required Electrical Service: Voltage/Amperage
49 R/A - 220V./30 Amp. - 440V./15 Amp.
65 R/A - 220V./42 Amp. - 440V./21 Amp.
100 R/A - 220V./60 Amp. - 440V./30 Amp.