If the amount of salt increase is greatly in excess of the amount shown below, it may be
advisable to install a voltage set-up transformer between the electrical source and the unit.
Prior to doing this, try changing the taps on the main transformer as shown in the wiring
Salometer readings may vary from one to five percentage points (saturation) due to individual variances between
salometers plus the added specific gravity of the hypochlorite.
VII. SYSTEM MAINTENANCE
Routine maintenance is relatively simple and consists of the following:
Daily, or as experience indicates, check the brine tank salt level. Add pure evaporated granulated salt as
Check the flowmeters (Rotameter), indicators and the DC Ammeter reading, Adjust water and brine feed
control if required. If the DC Ammeter reading is not in the full output range, consult the trouble-shooting section of the