Figure 3-3. Emergency Lighting Panel
Normal operating procedures
Make sure switchboard circuit breaker P13 is closed (ON) to provide power to power panel 3 (120 Vac).
On power panel 3(120 Vac), dose (ON) fuse box 13P13 to provide power to battery charger.
On battery charger, set HIGHFLOAT switch in FLOAT position for normal charging or in HIGH position for rapid
recharging of battery bank.
Do not allow battery charger to operate on HIGH warning for more
than 24 hours.
d. On power panel 3(120 Vac), dose (ON) circuit breaker 1 OP13 to provide holding voltage to inverter
and 120 Vac power to emergency lighting panel.
e. On inverter, move ON/OFF switch to ON position to place inverter in active standby.