a. Remove clamp (1), clamp (3A), and gasket (3B).
b. Remove basket strainer assembly from piping.
a. Lift basket strainer assembly (2) from strainer case (3).
b. Unscrew cap (4) and remove gasket (5) and seal (5A).
c. Remove overscreen (6).
d. Remove gasket (7) and preformed packing (8).
a. Replace any damaged or missing gaskets and preformed packing.
b. Replace inner strainer (9) or overscreen (6) if damaged.
c. Replace any missing or damaged components or between hardware.
d. Replace assembly if outer shell (3) is cracked or damaged.
a. Install preformed packing (8) and gasket (7) on inner strainer (9).
b. Install overscreen (6), gasket (5), and seal (5A) and screw cap (4) onto inner strainer (9).
c. Lower entire assembly (2) into outer shell (3).
d. Install basket strainer into piping system (para 3-22.1).
a. Place basket strainer assembly into piping.
b. Install gasket (3B), clamp (3A), and clamp (1).
4-198.2 Change 7