Wire the INCINOLET in accordance with the wiring
diagram shown in this manual. Metal conduit and
Association requirements. NOTE: Unit is grounded
through the green ground wire at the rear of the unit.
DO NOT install nor use the unit without providing
adequate ground according to this method. CAUTION:
UNIT MUST BE GROUNDED by means of conduit and
ground wire. Unit must be wired through 30 amp fuse or
Ventline is 4 inch diameter. single-wall construction.
and should be of corrosion resistant material such as
galvanized metal or stainless steel. Flexible. heavy-
duty. Neoprene coated line may also be used. provided
stainless steel hose clamps are used at each end of the
line to prevent leakage. Ventline joints within the toilet
room must be taped or otherwise sealed to prevent
leakage. Use caulking or tape around each ventline joint
including the elbow.
NOTE: DO NOT TERMINATE VENTLINE NEAR A
WINDOW OR FRESH AIR INTAKE
After installation, with electric power applied, test the
circuit by initiating the incineration cycle.
Blower comes on.
Indicator light comes on.
HOW TO USE.
To use the INCINOLET properly:
ALWAYS PLACE WAX PAPER LINER IN THE
BOWL BEFORE EACH AND EVERY USE.
Incineration starts automatically on footpedal flushing.
Length of incineration cycle may vary somewhat,
temperature. heater wattage, voltage and whether
incinerator is already hot from a prior cycle.