Electrical high voltage can cause serious injury or death. The test requires power to
be connected. Always take proper measures to ensure personal safety.
Run unit and check for excessive noise, vibration or overheating.
This motor is very heavy. Use care to avoid injury from attempting to lift or move the
Remove four nuts (1, Figure 2-84), Iockwashers (2) and washers (3). Motor is now free.
Attach suitable lifting device to eyebolt (4) and remove motor (5).
Remove four capscrews (6), washers (7), nuts (8), Iockwashers (9) and washers (10).
Remove motor mounting base (11).
Cable is removed at unit level but repaired at direct support.
a. Repair cable (para. 2-7).
b. Repair of motor or base is by replacement.
a. Mount motor mounting base (11), Secure with four capscrews (6), washers (7), nuts (8), Iockwashers (9) and
b. Attach suitable lifting device to eyebolt (4) and mount motor (6) onto mounting base (11).
c. Secure with four washers (3), Iockwashers (2) and nuts (1).