Figure 2-46. High/Low Pressure Lamps
If low or high-pressure switches shutdown the ROWPU automatically, they can
only be reset with the RESET switch. After emergency shutdown, distribution of
drinking water can still be made by pulling out the EMERGENCY STOP button
and running the distribution pump as required.
Go to control box assembly on the ROWPU. Locate the two lamps and switches for RAW WATER
Figure 2-47. Switches (Pump Controls)
d. Start RAW WATER PUMP NO. 1.
(1) Set switch upward to START.
(2) Hold switch up until green lamp No. 1 comes on.
(3) Release switch.